The revolution speed of the diesel engine is above its upper limit.
Languages: German | English | Chinese | Spanish | French | Symbolic
Elements of the Event page
|Event symbol||Consequences of the event|
|Error event||When an error event occurs, the monitored quantity has reached its error Limit. Error events shutdown the generator|
|Warning event||When a warning event occurs, the monitored quantity has reached its warning limit. Warning Events don’t shutdown the generator|
|Information event||An Information event is for information purpose only and has no effect on the generator operation|
|Device that triggers this event:||Generator control|
These symbols are used to warn of the possibility of personal injury of lethal danger during certain maintenance work or operations. See Users Manual for Safety Information and complete operating information. Read these instructions carefully. For further information click on the corresponding symbol. Each link opens a new tab.
Causes and solutions
|Common causes||Possible solutions|
|An incorrect setting of the servomotor can lead to a high engine revolution||Check the servomotor setting and correct the setting, if necessary|
|Defective servomotor||Check the servomotor and replace it, if necessary|
|An over-excitation can lead to a high engine revolution: The booster capacitors are permanently switched on because the booster relay is stuck||Check the booster relay and replace it, if necessary|
Distributors and Services
For any service or maintenance questions, please contact us or our worldwide partners.