The communication with the AGT module is interrupted once it was connected.
Languages: German | English | Chinese | Spanish | French | Symbolic
Elements of the Event page
|Event symbol||Consequences of the event|
|Error event||When an error event occurs, the monitored value has reached its error limit. Error events shutdown the generator|
|Warning event||When a warning event occurs, the monitored value has reached its warning limit. Warning Events don’t shutdown the generator|
|Information event||An Information event is for information purpose only and has no effect on the generator operation|
|Device that triggers this event:||Generator control|
These symbols are used to warn of the possibility of personal injury of lethal danger during certain maintenance work or operations. See Users Manual for Safety Information and complete operating information. Read these instructions carefully. For further information click on the corresponding symbol. Each link opens a new tab.
Causes and solutions
|Common causes||Possible solutions|
|Bus cable removed||Reconnect the bus cable|
|Loose contact or damage to the bus cable||Check the bus cable for loose contacts on the plug connections and for other damage (eg cable breaks due to kinks)|
|Bus termination is missing or incorrect||Check bus termination|
Distributors and Services
For any service or maintenance questions, please contact us or our worldwide partners.